Fittings for waster systems
Choose from different plastics, including ABS. Polypropylene and PVC. Support approximately every 500 mm horizontal tube. Approximately every 12 meters vertical pipe. Connected to a single system stack pipe bowl is limited to a maximum length of 3μm, unless special precautions (special automatic resealing trap design or with a separate ventilation duct systems, for example).
Flexible sewer basins and sinks are being provided particularly useful.
For joining the plain end pipe lengths together. The method can be used for all connections. Some socket has a blunt end to take another connector instead of the pipe.
For to see around corners “horizontal” pipe runs. 90 degrees and 135 degrees curved section is the most widely used. Garbage pipe should slope (but often just a little) toward the exit – will be connected to a vertical pipe with a 91 degree or 92 degree bend them. Some have blunt ends adjustable bending – rotating – bending are also available.
Common angles are 90,91,92 and 135 degrees. Tee generally sweep (in the T-shaped member should be assembled so that branched from the main pipe to the bending direction is the same direction of flow of water) in the flow direction. Avoid using links to connect two sewage pipes run in a single stack system wastes should be connected individually to the stack.
It can be used for various types of pipes connected to different connectors. Reducer can be used to engage 32 mm or 40 mm tube 40 mm or 50 mm tube. Copper compression can be used to connect plastic pipe to existing copper wastes. BSP screwed thread can be used to connect the tube to the waste outlet in the sink and so on. It can not be used in solder paste threads, but PTFE tape may be used as needed.
WC make a simple joint is a common end connector. This should be dry-jointed to the WC outlet, use a rubber gasket. Connectors various modes can have a different angle and length of sliding plug (depending on the location of toilets and sewage pipes to be connected). For particularly awkward joints, multi-KWIK connector can be used – again, a variety of patterns avail¬able, including a slight displacement cope with the pan outlet and the sewage pipe.
P traps have a horizontal outlet; S- trap has a vertical outlet. BSP threaded inlet traps usually have a direct connection to the waste outlets. Traps can light seal waste discharged into ditches or hopper head use; traps should be used in a single stack systems deep seal (75 mm). Deep seal traps take up more space, and you may need to install a cut under the floor bath. Bottle trap those tidy than the tube, may be easier to use in tight spaces, rather than deep seal trap – they should not be used in the waste. Bath traps often to complete the connection over¬flow system. Washing machine washing machine has a trap to take the side of the outlet hose import – replacing the sink trap trap. In some cases, automatically re-seal closure may be necessary – for example, for connection to a single stack system long basin waste.
Tags: a single system stack pipe bowl, ptfe tape, waster systems - Post Time: 02-18-16 - By: http://www.ptfetapechina.com